CL4FIRE RED Wrap Insulation
Canada’s National and Provincial building codes approved 38mm thick single layer wrap system for combining reduced and 0mm clearances for up to 2-hour ﬁre rating on grease duct, ventilation and metal pipes./
General Information – Product Description
CL4FIRE Wrap Products are manufactured using ﬂexible bio-soluble insulation calcium-magnesium-silica insulation blankets totally encapsulated in a ﬁber reinforced aluminum scrim jacketing. Please note in some jurisdictions, it is recommended that a mask be worn when handling bio-soluble blankets
CL4FIRE Red has been tested, certiﬁed and continually inspected by Quality Auditing Institute - QAI, a world renown independent third party laboratory servicing numerous global manufacturers. CL4FIRE Red is listed by QAI Laboratories and uniquely combined with evaluation 14372-R per the Canadian Construction Materials Division of the National Research Council of Canada to ensure conformance to all Canadian Building Codes.
Listed, tested and evaluated by QAI Laboratories for large steel ventilation duct sizes up to 218cm (86”) and width and up to 13,316 sq cm (2064 sq.in.) using a single layer of nominal 38mm (1 ½”) thick x 96 kg/m3 (6 pcf).
Requires 38mm (1 ½) nominal thickness for ventilation ductwork and metal piping. Also approved using nominal 76mm (3”) thickness for grease duct and metal fuel piping such as diesel and natural gas.
Features and beneﬁts
CL4FIRE Red insulation blanket is a lightweight, high temperature, bio-soluble calcium-magnesium silica insulation blanket that is fully foil encapsulated and bonded to the ﬁberglass reinforced scrim to ensure a secure and responsible installation without gaps. It is designed to be installed using weld pins, steel banding or a combination of both fastening methods as outlined in QAI listed systems F405-1-1, F405-1-2 and F405-1-4 and as outlined in NRC – Canadian Construction Materials Division (CCMC) evaluation 14387-R.
CL4FIRE Red meets CAN/ULC S-102 building code required ﬂame spread index < 25 and a smoke development value of < 50.
Listed and building code reviewed for single layer 38mm (1 ½) thick application on ventilation ductwork and non-fuel metal piping for up to a 2-hour ﬁre rating.
Listed and building code reviewed for 76mm (3”) thick application on grease ductwork, generator exhaust, and metal fuel piping for up to a 2-hour ﬁre rating when installed per QAI listed system F405-1-4 and CCMC 14382-R. Evaluated for use as 2nd 38mm (1 ½”) layer which can be intermittently applied in combination with CL4FIRE CODE-96 38mm (1 ½”) thickness blanket insulation.
Together these products oﬀer a unique zero clearance, thin, safe and easy to install grease duct system speciﬁcally designed and approved for Canadian Building Codes installations.
Codes and Standards
CL4FIRE Red meets the following standards testing to requirements outlined by the National Research Council of Canada’s Construction Materials Division as necessary for meeting Canadian building codes. See CCMC evaluation 14382-R for additional information.
CCMC Evaluation 14382-R combined with a Ministers ruling for the Ontario Ministry of Municipal Aﬀairs & Housing Evaluation is required for ﬁre protection of ventilation ductwork, metal piping and grease duct for reduced clearance to combustible materials because there is no Canadian building code referenced standards for ventilation duct or metal pipe CCMC is the only agency that can oﬀer evaluation for grease duct reduced clearances to combustible materials because the CAN/ULC S144 grease duct testing standard only outlines testing for zero clearance to combustibles.
NFPA-96 – Standard for Ventilation Control and Fire Protection of Commercial Cooking Operations
CAN/ULC S144 Standard Method of Fire Resistance Test – Grease Duct Assemblies
ISO 6944 – 1985 Duct - A – Fire Resistance Tests – Ventilation Duct
CAN/ULC S115 Standard Method of Fire Tests of Firestop Systems
CAN/ULC S102 Standard Method of Test for Surface Burning Characteristics of building materials
ASTM E2336 Standard Test Methods for Fire Resistive Grease Duct Enclosure Systems (superseded in Canada by CAN/ULC S144 standard)
ASTM E 119 – Standard Test Methods for Fire Tests of Building Construction and Materials
ASTM E 84 – Standard Test Method for Surface Burning Characteristics of Building Materials
ASTM E 814 (UL 1479) – Fire Tests of Through-Penetration Fire Stops Standard
CAN/ULC S135 - Standard Test Method for The Determination of Combustibility Parameters of Building Materials
CAN/ULC S702 - Standard for Mineral Fiber Thermal Insulation for Buildings
ASTM C411 Standard Test Method for Hot-Surface Performance of High-Temperature Thermal Insulation
ASTM C356 – Standard Test Method for Linear Shrinkage of Preformed High-Temperature Thermal Insulation Subjected to Soaking Heat
ASTM C1136 – Standard Speciﬁcation for Flexible, Low Permeance Vapor Retarders for Thermal Insulation
ASTM E96 – Standard Test Methods for Water Vapor Transmission of Materials
ASTM E1371 Standard Test Method for Determination of Emittance of Materials near Room Temperature Using Portable Emissometers
ASTM C518 Standard Test Method for Steady-State Thermal Transmission Properties
ASTM C1338 Standard Test Method for Determining Fungi Resistance
ASTM C665 Standard Speciﬁcation for Mineral-Fiber Blanket Thermal Insulation for Light Frame Construction and Manufactured Housing
Specificaons – Division 12 07 00
Product shall be stored in sealed original moisture resistant packaging prior to use.
CL4FIRE shall be installed by a qualiﬁed contractor in strict accordance with QAI listed systems or CCMC 14687-R evaluation requirements.
Grease duct access doors must be CL4FIRE Red protected with installation per manufacturers detailed requirements.
12mm (1/2”) wide stainless steel banding must be installed using tensioning tool and crimped with stainless steel banding clips.
Where required steel insulation pins must be capacitor discharge gun welded to exposed or underside of ductwork on maximum 304mm (12”) centers and maximum (6”) from the edge of duct.
2 or 3 sided applications may be installed only when the gap between the substrate and duct or pipe does not exceed 102mm (4”)
Should a transition be required from a gypsum shaft system to a CL4FIRE Fire Protection Thermal Insulation installation, the annular space around the duct and the shaft must be ﬁlled to a minimum of 102mm (4”) depth of CL4FIRE insulation and topped with a 6mm (1/4”) depth of sealant ﬂush with the surface of the gypsum.
Grease duct zero clearance installations must be installed using minimum 76mm (3”) thickness of CL4FIRE Red installed to
QAI listed system F405-1-4 listed system requirements.
Grease Duct maximum 230mm (9”) clearance from the ductwork to combusble applicaons must be installed using
CCMC 14387-R detail as outlined in Appendix A of the CCMC document.
Venlation ductwork or metal non-fuel piping must have a single layer of CL4FIRE Red 1 1⁄2” thick installed to QAI listed system
F405-1-1 as follows:
♦ For up to a 1-hour fire rang CL4FIRE Red may be installed using snugly buCed seams or 76mm (3”) overlaps throughout
♦ For up to a 2-hour fire rang CL4FIRE Red must be installed using 76mm (3”) overlaps throughout
Metal Fuel Piping
Metal fuel-piping such as natural gas and diesel must be installed using a minimum of 2 layers of 38mm (1 1⁄2”) CL4FIRE Red
installed with seams staggered a minimum 76mm or (3”).